YOUR GUIDE TO WIRING AND CONNECTION OF SOLAR PANELS
A typical commercially available photovoltaic panel is rated between 50 and 300 watt. Given the fact a typical household needs several kilowatt, a single panel obviously is not enough for an entire house. To increase net power level multiple modules are connected into arrays. There are three main wiring configurations
(see wiring diagrams below):
To wire the panels in series
you connect the positive terminal of one device to the negative
terminal of the next one.
With this connection, voltage adds and current stays the same as a single panel.
To wire the panels in parallel
you connect together the terminals of the same polarity. With such connection the resulting output voltage stays the same as a single module, and amperage adds.
connection, two or mores series strings are paralleled. In such a scheme both voltage and current increase. Assuming all modules are identical and receive exactly the same amount of sunlight:
Vout ≈ n×V
Iout ≈ m×I,
where V and I - voltage and current of each individual module respectively, n - number of modules in each series string; m - number of paralleled groups.
The connection of the strings is usually done in a combiner box. Ideally, each series circuit is fused separately. However, if you properly sized the conductors, you can protect several (probably up to three) circuits by a single fuse.
MAIN WIRING CODES AND STANDARDS
The main generic document in US that governs most electrical installations is National Electric Code® (NEC®)
. It is updated every three years by National Fire Protection Association (NFPA®). Although technically NEC is purely advisory, it is used nationwide as a de-facto standard. Nevertheless, the local authority that are enforcing the code, may waive its specific requirements or allow alternative installation methods. Therefore it is always advisable to check with the local codes as well.
of NEC® covers specifically wiring of solar energy systems. Other articles such as 110, 250, 300, 310, 480, and 702 may also apply. Consult with the latest NEC and local codes for all design decisions. Here is a quick checklist of some important facts to remember:
REFERENCES AND ADDITIONAL INFORMATION:
- PV circuits shall not be run in the same cables or raceways with non-PV systems unless they are separated by a partition.
- PV wires should be identified and grouped, particularly you have to group separately DC and AC lines.
- DC buses from grounded panels must be protected with a DC ground fault interrupter.
- Solar panel voltage increases at lower temperatures. Therefore in order to determine voltage rating of cables, disconnects and other equipment, you have to consider open circuit voltage of the arrays at the lowest possible ambient temperature in your area. Depending on your location, the voltage correction factor can be up to 1.25.
- When you size circuits for their current rating, you need to find maximum short circuit current depending on your connection scheme (see diagrams above) and multiply it by 1.25 (i.e. add 25% margin). Note that the cells produce more current the colder they get. Given the fact that Isc is stated at 25oC, you need to add another current correction factor based on coldest possible operating temperature expected. This factor can be up to 1.25. As the result, the conductors have to be sized for up to 1.56×Isc.
- If DC bus voltage in house wiring exceeds 80V, you need to install a DC arc-fault circuit interrupter.
- DC conductors should have a disconnect switch or a circuit breaker.
- Wires in accessible places with voltages above 30V and all wires inside home should be run in raceways.
- Beneath the roof the wires should not be closer than 25 cm (10") to the roof decking.
- If you have more than 50V coming out of the PV system, generally, one of the DC buses have to be properly grounded in a single point as close as possible to the panels. However, the transformerless systems can be exempt from this requirement if they comply with NFPA 70® 690.35.
- Regardless of the voltage, metal frames of the solar panels and all equipment should be grounded.
- Generally, the DC voltage from PV can be up to 600V. However, if you use a system with battery backup, the battery bank's nominal voltage should be below 50V, unless exposed parts with higher voltages are not accessible during normal battery maintenance.
for photovoltaic systems installation.